Walkable grille with 0° angle deflection.
With flow control damper OD total depth = 48 mm + 45 mm.
In addition to standard sizes, other sizes can be specially ordered. The maximum size is 1500×300 mm (LxH).
It is possible to have a continuous grille of modular design when the installation length is greater than 1500 mm. The maximum total length is 20 m.
|Installation frame||Galvanised steel||–|
The bevel angles of the outer frame have been welded so that the joints are almost invisible.
|Model with removable
|AV||Vanes can be removed to
allow access to plenum
|Flow adjustment damper||OD||Aluminium opposite blade
damper for airflow adjustment
|Installation frame||IF||For the installation of the grille|
|Concealed screw fastening||CC||For installation with IF frame|
|Visible screw fastening||SF||Screw fastening with 25 mm wide frame|
|Flat installation frame||A||18 mm wide – 48 mm high frame|
|Rounded installation frame||B||25 mm wide – 48 mm high frame|
Supply air is supplied without deflection through the horizontal vanes into the space. Supply air mixes with room air in front of the grille.
The Halton FLU grille can also be used as an exhaust unit.
The Halton FLU grille has a high load resistance, with a class K3 according the standard NF-EN 1253-2, (test report CSTB n°CAPE AT 16-009).
The class K3 is defined in the standard as: “Area without at the vehicle traffic, like common place, shopping centers, and some public buildings”
The grille is connected to the floor plenum using the IF installation frame. (1).
The grilles are supplied with clips fastening as standard with the IF installation frame.
Concealed screw fastening is possible when the grille is installed with an installation frame (IF).
Visible screw fastening is possible with the 25 mm wide frame.
The auto screws, 4.2×25 (bevel headed screw) are supplied.
The size of the installation hole is LxH when an installation frame is used, and (L-5)x(H-5) without an installation frame.
The airflow rate is adjusted by turning the damper blades behind the grille with a screwdriver. The measurement is carried out when the grille is installed.
The grille can be removed for cleaning.
Remove from the floor, by gently pulling the grille from the outer frame. Use a screwdriver, if necessary.
Clean the components with a damp cloth. They must not be immersed in water.
Push the grille back into place, so that the springs lock.
The floor grille has horisontal fixed vanes without deflection, and an 18 mm wide flat or 25 mm rounded frame, with an anodised standard finishing.
The floor grille can be used for both supply or exhaust air.
The bevel angles of the outer frame is welded so that the joints are almost invisible.
The floor grille is mechanically strong in order to bear external loads.
The floor grill is detachable in order to provide access to the duct.
S = Frame option
A Frame 18 x 45
B Frame 25 x 45
L = Length (mm)
200, +1, .., 20000
H = Height (mm)
100, +1, .., 300
FS = Fastening
CC Concealed screw fastening
SF Screw fastening
FI = Finishing
MF Mill finished
ZT = Tailored product
Y Yes (ETO)
IF Installation frame (Grilles)
OD Opposed blade damper (Grilles)
FLU/A-200-100, FS=CL, FI=AN, ZT=N